Fire Department Requirements for Subdivisions
Emergency Access shall be provided and maintained at all times during construction.
Street Signs shall be permanently mounted at all street intersections and shall display the correct street name and block number. Street signs shall meet City of Midlothian standards and installation requirements.
Fire Hydrants shall meet City of Midlothian standards and installation requirements, be operational and properly painted. The “Steamer” outlet size shall be 4.5” NST. The paint scheme shall be per Midlothian Fire Department standards:
|12" or larger main||Blue bonnet, silver barrel and caps|
|8" main||Green bonnet, silver barrel and caps|
|6" main||Silver bonnet, silver barrel and caps|
|Private main||All red|
|CO-OP water||Red bonnet, silver barrel and caps|
Fire hydrants shall be located at every intersection and between intersections so the distance between hydrants along the street does not exceed 400 feet. The “Steamer” outlet of the hydrant shall face the street and the hydrants shall be mounted 3-5’ back from curb with the bottom flange at or slightly above grade level.
Fire Hydrant Reflectors shall be mounted on the road surface to indicate the location of the hydrant. At intersections there shall be a reflector mounted in each street of the intersection. The reflectors shall be Blue in color, 4”x4” in size and mounted in the center of the lane closest to the hydrant.
Model Homes may be constructed before final subdivision acceptance is received if the following criterion is met.
- Two or more fire hydrants closest to the model home site are operational.
- Street signs at entrance into subdivision and at the model home site are permanently mounted and meet the same standards as stated above.
- Acceptance from the Fire Department and Engineering Department is approved.
Amenity Centers and Neighborhood Swimming Pools shall have Knox Box containing gate and building keys installed for emergency access, a 2A:10B:C or larger fire extinguisher mounted and an operational emergency 9-1-1 telephone.
Acceptance by both the Fire Department and the Engineering Department is required before any construction of homes or other occupancies can begin.
Fire Marshal (972) 775-7662 Engineering (972) 775-7199